Honeywell Hunter 44100A Owner's Manual
Owners Manual Model 44100A
Your new Climate Technology thermostat will provide years of reliable service. Using this digital thermostat will provide more uniform comfort in your home through the seasons. Thank you for buying a Cli- mate Technology product!
Please read this manual for complete instructions on installing and operating your thermostat. If you require further assistance, call Cli- mate Technology Technical Support at 1-800-676-7861 from 8am to 5pm Central Time.
We are pleased you have selected one of our broad line of home comfort products. Our products are manufactured to high quality standards and are designed for years of service. We hope you will be satisfied and thank you for buying a Hunter product.
Table Of Contents
Remove Old Thermostat 8
Labeling Wires 10
System Selector Switches 14
Connecting Wires and Mounting Thermostat 14
Programming/Setting Clock 16
Personal Program Schedule 20
Reviewing Program Settings 24
Manual Overide 25
Filter Monitor 28
Temperature Span 29
Trouble Shooting Guide 30
Typical Wiring Diagrams 32
Read This Before Installing Thermostat
Read the entire installation section of this Owner’s Manual thoroughly before you begin to install or operate your Hunter Thermostat.
Remove the mylar label from the display window.
2. INSTALLATION Honeywell Hunter 44100A
All installation is normally performed at your thermostat.
3. PROGRAMMING Honeywell Hunter 44100A
You can practice programming before installing your thermostat by inserting and connecting the batteries and following the instructions on page 14. This can be done while you relax in your favorite chair and is a very good way to familiarize yourself with all the functions of your Hunter Thermostat.
4. OPERATION Honeywell Hunter 44100A
Your Hunter Thermostat is designed to operate with most gas, oil, electric or 2-wire hot water heating, and air conditioning systems that have 24-volt or millivolt control. This Hunter Thermostat will not control multistage heating or cooling systems, 110/220 V systems, or 3 wire zone systems.
5. COMPRESSOR PROTECTION Honeywell Hunter 44100A
The thermostat provides a 4-minute delay after shutting off the compressor before it can be restarted. This feature will prevent damage to your air conditioner compressor caused by rapid cycling. It does not provide a delay when there are power outages.
6. TEMPERATURE RANGE Honeywell Hunter 44100A
Your thermostat can be programmed between 40°F and 95°F (5°C and 35°C). However, it will display room temperatures from 32°F to 99°F (0°C to 37°C).
7. POWER FAILURE Honeywell Hunter 44100A
Whenever the main power is interrupted or fails, the battery power retains the programs and current time.
What You Need
This thermostat comes with two #8 slotted screws and two wall anchors for mounting. To install your unit, you should have the following tools and materials.
• Two 1.5 V (AA) Size Alkaline batteries
• Electric drill and 3/16" bit
• Slotted screwdriver
INSTALLATION Honeywell Hunter 44100A
Remove Old Thermostat
CAUTION: Do not remove any wiring from existing thermostat before reading the instructions carefully. Wires must be labeled prior to removal.
- IMPORTANT!Turn off the power to the furnace at the main power panel or at the furnace.
- Remove existing thermostat cover and thermostat. See Figure 1. Some thermostats will have screws or other locking devices that must first be removed. Once wall mounting plate is exposed, look for wires.
If wires are not visible, they may be connected to the back of the wallplate. Again, look for screws, tabs, etc. Some models have doors that open to expose wires and mounting screws. (See Figure)
Read More Honeywell Hunter 44100A Owner's Manual on PDF Below