Honeywell Series 2000 Commercial Thermostat Subbases
The 07300 Thermostat Subbases are used with T7300 Thermostats to provide electronic control of commercial 24 Vac Single or multistage heat pump or convenbonaJ heating and cooling systems. Select modeS have terminals tor LEDs and remote temperature sensors. Heterto I able 1. All Q7300 1 hermostat Subbases requre a common wire to the supply power.
Table 1. Description of 07300 Subbases.
Honeywell Series 2000 INSTALLATION
When Installing this Product...
- Read these instructions carefully. Failure to follow the Instrudlons can &mage the product or cause a hazardous condition.
- Check the ratings given In the Instructions and on the product to make sure the product S sutable for your application.
- Installer must bea traned, expenenced service technician.
- Atter completing Installation, use these Instructons to check out the product operation.
Honeywell Series 2000 INSTALLATION Location
Subbase without Remote-Mounted
Install the thermostat about 5 tt (1.5m) above the tloor In an area with good air circulation at average temperature. See fig. 1. Ch not nstall the thermostat where it can be affected by: drafts, or dead spots behnd doors and In comers hot or cold air from ducts radiant heat from sun or appliances oncealed Pipes and chimneys. unheated (uncoded) areas such as an outsoe wall behhd the thermostat.
If only the remde-mounted temperature sensor(s) is used to sense and ontrol room temperature, then Install the thermostat In an area that IS accessible for setlng and adjusting the temperature and settings. If both the subbase and remde-mounted temperature sensor(s) are used to sense and control room temperature, then Install the subbase about 5 tt above the tloor In an area witl good air circulation
Readmore and Download Honeywell Series 2000 Commercial Thermostat Manual
|Title||: Honeywell Series 2000 Commercial Thermostat User Manual|
|Pages||: 8 Pages|
|File Size||: 10 MB|